ESD Flooring Is A Floor
ESD Flooring is a floor
ESD Flooring, also known as a dissipated electrostatic floor, is a floor that, when grounded or connected to any lower potential, allows the charge to dissipate, with a resistance of 10 in the order of 10 to 10 Between the characteristics. "GB50174-2008 electronic information system room design specifications" page 20 8.3.1 provides: ESD Flooring or floor surface resistance or volume resistance should be 2.5 × l04 ~ 1.0 × 109Ω.
ESD Flooring Features
Computer room anti-static technology, is part of the scope of room safety and protection. Static problems caused by the hardware is not only difficult to detect, and sometimes make the software staff mistaken for software failure, resulting in confusion. In addition, static electricity through the human body when the computer or other equipment discharge (the so-called ignition) when the energy to a certain extent, will give people the feeling of electric shock (for example, sometimes touch the computer monitor or chassis)
Note: ESD Flooring laying, be sure to carry out anti-static grounding and then protect the resistance box, or can not achieve anti-static effect.
ESD Flooring Selection method
1, the first need to accurately calculate the total number of ESD Flooring of the building room (or the number of blocks) and a variety of accessories (standard bracket ratio of 1: 3.5, standard beam ratio of 1: 5.2) and the remaining So as to avoid waste or shortage.
2, fully understand the manufacturers of ESD Flooringing produced by the variety and quality, and a variety of technical performance indicators.
The technical performance of ESD Flooring mainly refers to its mechanical properties and electrical properties. Mechanical properties of the main consideration of its carrying capacity, wear resistance.
3, should be the engine room all the equipment in the heaviest equipment on the basis of the weight to determine the ESD Flooring load, which can prevent some of the equipment caused by excessive deformation of the floor or damage.
4, ESD Flooring by the impact of external environmental conditions change small. That is, because the external environment temperature is too high, too low a significant expansion and contraction, that is, when the room temperature is slightly higher, ESD Flooring expansion expansion, can not be removed and replaced; low temperature ESD Flooring shrinkage, resulting in loose feeling. ESD Flooring by the environmental impact of shrinkage should be less than 0.5mm, plate deflection should be less than 0.25mm.
5, ESD Flooring surface should not reflect, do not slip, corrosion-resistant, dust-free, no dust, easy to clean.